Jan 7, To obtain the NPAG book, by download or CD-ROM, please use the contact form Jan 7, In order to provide the modern practicing substation engineer with reference material, AREVA’s Network Protection & Automation Guide. Alstom NPAG Network Protection & Automation Guide – New still sealed. EUR ; + EUR postage. MITZ N MITZ01L1AAB ALSTOM.
|Published (Last):||13 October 2005|
|PDF File Size:||19.67 Mb|
|ePub File Size:||12.32 Mb|
|Price:||Free* [*Free Regsitration Required]|
Chapter 01 Introduction The change in protection technology, together with significant changes in Utility, Industrial and Commercial organizations, has resulted in new emphasis on Secondary Systems Engineering.
Arevx, new chapters covering the fields of power system measurements, power quality, and substation and distribution automation are found, to reflect the importance of these fields for the modern power system engineer.
Search – Schneider Electric
Permanent faults, such as broken conductors, ageva faults on underground cable sections, must be located and repaired before the supply can be restored. Premium Membership Get access to premium electrical guides, technical articles and much more!
Such equipment can arev cause and be affected by electromagnetic disturbances. Motor characteristics must be carefully considered when applying protection; while this may be regarded as stating the obvious, it is emphasised because it applies more to motors than to other items of power system plant. Chapter 24 Substation Control and Automation The sometimes complex interlocking and sequence control requirements that are to be found in a substation of any significant size lend themselves naturally to the application of automation.
Chapter 05 Equivalent Circuits and Parameters of Power System Plant Knowledge of the behaviour of the principal electrical system plant items under normal and fault conditions is a prerequisite for the proper application of protection.
Areva Npag Index – [PDF Document]
At the other end of the scale, a domestic user of a PC has to re-boot the PC due to a transient voltage dip, causing annoyance to that and other similarly affected users. The first part of the book deals with the fundamentals, basic technology, fault calculations and the models of power system plant, including the transient response and saturation problems that affect instrument transformers. Protective Relays, Measurement and Control Since aerva, the Network Protection and Automation Guide formerly the Protective Relays Application Guide has been the definitive reference textbook for protection engineers and technicians.
Therefore, transporters and users of electrical energy have become much more interested in the nature and frequency of disturbances in the power supply.
The cause of the fault would not be removed by the immediate tripping of the circuit, but could be burnt away during a time-delayed trip. Thank you for posting this tutorial! Chapter 09 Overcurrent Protection for Phase and Earth Faults Protection against excess current was naturally the earliest protection system to evolve.
Chapter 16 Transformer and Transformer-Feeder Protection The considerations for a transformer protection package vary with the application and importance of the transformer. Chapter 14 Auto-Reclosing Faults on overhead lines fall into one of three categories: Shoukat Ali Jun 10, Chapter 15 Busbar Protection The protection scheme for a power system should cover the whole system against all probable types of fault.
Transient faults are commonly caused by lightning and temporary contact with foreign objects.
Unrestricted forms of line protection, such as overcurrent and distance systems, meet this requirement, although faults in the busbar zone are cleared only after some time delay. Additionally communications facilities are also required when remote operation of a circuit breaker is required as a result of a local event.
Unit schemes of protection that compare the conditions at the two ends of the feeder simultaneously positively npav whether the fault is internal or external to the protected section and provide high-speed protection for the whole feeder length. Sincethe Network Protection and Automation Guide formerly the Protective Relays Application Guide has been the definitive reference textbook for protection engineers and technicians.
Glad you like it! Chapter 13 Protection of Complex Transmission Circuits For economic reasons, transmission and distribution lines can be much more complicated, maybe having three or more terminals multi-ended feederor with more than one circuit carried on a common structure parallel feeders.
eBook NPAG 2012 – Windows Application – Network Protection & Automation Guide
A power system is normally treated as a balanced symmetrical three-phase network. This represents a tremendous achievement for all those involved in relay design and manufacture.
Chapter 21 Relay Testing and Commissioning The testing of protection equipment schemes presents a number of problems. Chapter 07 Relay Technology The last thirty years have seen enormous changes in relay qreva. By using symmetrical component analysis and replacing the normal system sources by a source at the fault location, it is possible to analyze these fault conditions.
Other possibilities are the use of series capacitors or direct-connected shunt reactors. Knowledge of the behaviour of the principal electrical system plant items under normal and fault conditions is a prerequisite for the proper application of protection. The intention is to make NPAG the standard reference work in its’ subject area – while still helping the student and young engineer new to the field.
Unit protection schemes, formed by a number of relays located remotely from each other, and some distance protection schemes, require some form of communication between each location in order to achieve a unit protection function. A modern generating unit is a complex system comprising the generator stator winding, associated transformer and unit transformer if presentthe rotor with its field winding and excitation system, and the prime mover with its associated auxiliaries.
Many of the techniques pnag have been evolved for EHV power systems may be applied to lower voltage systems also, but typically on a reduced scale. Traction unit faults are a fire hazard and a safety zreva to passengers, especially in tunnels.
The performance of measuring transformers during and following large instantaneous changes in the input quantity is important, in that this quantity may depart from nlag sinusoidal waveform. This is because the main function of protection equipment is solely concerned with operation under system fault conditions, and cannot readily be tested under normal system operating conditions. Premium Membership Premium membership gives you an access to specialized technical articles and extra premium content electrical guides and software.
This includes a new chapter on the protection of a. The consequences of an occasional unwanted trip are far more acceptable the control centre simply recloses the tripped CB, some trains are delayed while the control centre ensures it is safe to reclose than the consequences of a failure to trip for a fallen wire or a traction unit fault.